Rocburn were chosen to supply the smoke ventilation equipment to be installed as part of renovation works for The Balmoral Hotel, Harrogate. This was to renovate AOV systems to bring them up to current standards.
This job consisted of 1 stair core ventilated by a 1mtr square smoke ventilation pitched velux rooflight, with lobbies on the Ground, 1st 2nd, 3rd and 4th floors.
Each lobby had a damper and grille fitted to ventilate smoke into an assigned smoke shaft.
The control panel was wired back to an addressable fire alarm, which would trigger on smoke to open the damper on the fire floor along with the related skylight. This automatically cleared the communal escape routes of smoke.
The smoke ventilation equipment was specified in accordance with Approved Document B.
1mtr square free vent area smoke ventilation pitched rooflight EN12101-2 rated
Local fireman’s override switch in lobby corridor, used to manually override the fire alarm signal to open or close the AOV from within each zone
EN1366-2 Tested Dampers and Grilles:
Multi Zone Fire Alarm, Fitted Recessed in the wall
This is one of the many multizone projects we have supplied smoke ventilation equipment for.
For advice please contact one of our sales team either using the form below, by email [email protected] or calling us on 01702 826 267.